This is a comprehensive report given by Stan Martenson. Stan and I have walked and discussed the course's drainage problems. This report outlines our major drainage issues and takes into account the numerous times we have had to cancel events due excess water on the golf course. We all know that after heavy rainfall the golf course is closed. This report gives us both the problems and possible solutions to fixing our drainage issues. I thank Stan for his hard work on this matter and hope you read the document he wrote below:
Ridgeway Drainage Solutions by Stan Martenson
I have been on the Greens and Grounds Committee for 4-5 years. I am a Civil Engineer and work with drainage year round. In addition to normal G&G activities, I joined G&G to help solve drainage issues in 4 areas:
• Regular ponding on the north side of 18 near the fairway tree
• Regular ponding on 11 in front of the silver tee box
• Frequent ponding on 11 at the bottom of the range
• Frequent ponding in 3 fairway low area
After many flooding occurrences, I convinced Tom Wenzel to mark up a course map with the sprinkler system to show all drain tiles lines he was aware of as best he could. I finally got the map in late 2009, transferred the info to AutoCAD, and can reproduce, add to, or change as needed. Discussions in 2010 and early 2011 centered on “Do we have blockages caused by siltation or from damage caused by the sprinkler system installation?”
I found the answer this summer when the Saturday morning Red Coat was postponed. I knew we had heavy rain in the early morning. When I got the e-mail that the course was closed, I headed out to Ridgeway to walk around. AMAZING!!
I had known for a couple years that the Ridgeway Drive residential area SE of the maintenance building drains through the golf course in a 12” pipe. When I got to the course, I couldn’t find the pipe inlet on Ridgeway Drive, water was coming OUT of the manhole on the east side of 12 fairway, the drains on 11, and the drains on 3. The discharge west of 16 tee box sounded like a raging river. I now call it “Trying to put 20#’s of shit in a 5# bag.” Steve Blake and I spent a couple hours looking at various situations and monitoring water flow off the course.
Conclusions and Solutions
The main drain is not plugged. It is too small. Field survey work is completed and we are looking at preliminary sizing. We have good slope across the course. The Town of Clayton is looking at street improvements in the Ridgeway Drive area. We hope to work cooperatively with them to install a new drain across the course in fall of 2012 that is sized to serve both our needs.
The drain in front of 11 silver tee is just a stone sump. A new tile line will be trenched in when time and budget permits.
The ponded area on the north side of 18 can be tiled to existing tile on the south side by the treatment plant when time and budget permits.
The ponded area on 11 at the bottom of the range is drained by 2 – 8” tile to the #12 manhole. Additional evaluation will be made to see if more capacity is needed or if a larger main drain will solve the problem.
The cost of implementing the solutions will be more than offset by saving one large event.